Straight through tubes with no u-bends means that you can clean out the entire tube length and see light at the other end of the tube for complete heat exchanger cleaning.
Water is an excellent heat transfer medium when cooling liquids to temperatures unattainable by air-cooled systems. However, hot gas systems are, by nature, of extreme temperatures and not a good application for water-cooled systems. Thermal shock, liming and plating-out in the heat exchangers are serious consequences. The dangers of the cooling water flashing to steam […]
…of accumulated debris because you dispose of only the debris and not expensive filter cartridges. Typically, a ten pound cartridge will only accumulate ten pounds of debris.
…because it contains only one moving part …the debris level sensor. With one moving part and no filter cartridges to replace, maintenance will be an expense of the past.
…because it’s only power consumption is a small pressure drop through the separator. All the work is done by centrifugal force and gravity.
…because it will splice into most existing circulating systems. Virtually any system can run cleaner and more efficiently by simply adding a Sludgebuster after the circulating pump. The only power requirement is a 110-volt connection to the level indicator in the debris receptacle.
…because of our simple, trouble-free design. When compared to systems designed for similar flows, a Sludgebuster system will save thousands of dollars
1. Dirty liquid, driven by the circulating pump, enters the separator’s tangential inlet and is directed into a spinning motion. 2. Spinning motion imparts centrifugal force on the solids entrained in the liquid. This centrifugal force throws the debris to the outside wall of the separator. 3. The friction of the flow rubbing against the […]
Moisture can cause dramatic shifts in the cooling curve of oil, resulting in unwanted metallurgical variations. The AQUA-SENSE system constantly monitors moisture levels, and will sound an alarm and give a visual signal when predetermined limits have been exceeded. Early detection and correction before moisture alters the cooling curve of the oil can stop production […]
An undetected leak in a water-cooled heat exchanger, bearing, top cool section or even a building roof may lead to the accumulation of water in a quench tank. When hot steel hits water accumulated in the bottom of the tank, the water will turn to steam and drive the oil in the tank up into […]